- WP Max Heat Pumps
- Stratified storage tank
- Solar Thermal Energy
- Heating + Cooling with photovoltaics
- Domestic hot water heating
- Control technology
Drinking water heating using the flow-through principle is the optimum solution for buildings where there is a high demand (e.g. hospitals, hotels, sports facilities, etc.) and high drinking water hygiene must be ensured. Cascading ensures a high level of control accuracy for a wide range of drinking water requirements - from the use of only one extraction point to peak loads.
Flow rate: 75 - 150 l/min
Technical measures for the reduction of Legionella growth according to the drinking water ordinance must be observed in large plants. Accordingly, systems with a drinking water volume of more than 400 l and/or a pipe volume greater than 3 l between the drinking water heating outlet and the tapping point must be uniformly heated to at least 60 °C everywhere at least once a day. In addition, the temperature in the circulating hot water system must not be more than 5 degrees below the storage tank outlet temperature. The larger the volume of hot drinking water stored, the more heat energy is required by the prescribed sterilisation of the system. Our fresh water technology performs these tasks very efficiently and reliably in combination with the corresponding control technology.